|Prime Power (PRP)||19.0 kVA|
|Standby Power (LTP)||20.0 kVA|
|Power Factor||0.8 φ|
No, the price doesn't include installation. Installations are all different and require varying length of cable, time and distances to be travelled. In addition to this installations need to be done by a qualified electrician to issue a valid Certificate of Compliance (COC) for your insurance. We will gladly recommend a qualified local installer, please ask your Sales Consultant for more information.
No, but we do have recommended installers throughout Southern Africa who will be able to assist you with your installation and sizing your generator.
All prices exclude delivery. Due to the nature of the goods and their size they have to be delivered by a specialised truck and rigging crew. Hence delivery is charged extra based on the distance and complexity of the delivery.
Yes, you'll need either an Automatic (ATS) or Manual change over switch in order to link the generator into your properties electrical distribution board.
The recommended size ATS is based on the size of the generator, not the mains incoming supply. The ATS should be capable of taking the whole load from either mains or the generator as both will pass through the ATS switch. Therefore, whilst the recommended switch size will be correct for most installations, it may not be correct for your installation. You should ensure that an electrician performs a load test and checks this information.
The warranty is 6 Months or 500 Hours whichever occurs first. It is a limited warranty. Travel to site is not included in the warranty. The goods need to be returned to us or a call out will be charged. Please refer to the Terms and Conditions of sale and the Warranty Card for further information on the warranty.
Pricing is valid whilst stock lasts and is subject to change without prior notice. Pricing on the website is indicative and should always be confirmed by Jaeger Projects in the form of a written quotation.
The DKG-116 controller is not recommended for use with inverters. Whilst it has been tested with some inverters, Harmonics is an issue that can cause the generator and inverter not to work well together.